Assuming that acceptance testing is completed using the P.E.’s specifications, manufacturer’s recommendations and the minimum requirements of NFPA 110, and the machine is pronounced healthy; you are to proceed with the maintenance and testing program the next day as if the EPSS had been there for years.
Emergency Power Blog
Who has the last word on maintenance and testing requirements? NFPA 110, 8.1.1 is essentially the genesis of all maintenance and testing (M/T) programs. Why? Because while other standards are concerned with maintenance and testing, all refer to NFPA 110, and paragraph 8.1.1 marks the beginning. This paragraph is just one sentence in length, but […]